required ANSI Z358.1-2009 are eyewash bottle stations are required to provide on-the-spot decontamination. Accidental chemical exposure can occur in the workplace, and while personal protective equipment should beware of chemical splashes, decontamination equipment be available as a backup.
When an employee is required to use eye or face wash equipment, he or she flushes the body concerned immediately with a large supply of clean fluid – water or other materials – under low pressure. The liquid dilutes or blows away the material but not disable it.
15 minutes is generally time for flushing chemical, but more or less needed. If the substance is mildly irritating, only five minutes necessary. 20 minutes is needed for moderate to severe irritant and non-penetrating corrosives. 60 or more minutes required for penetrating corrosives and acids. If the material is not fully flush, keep repeating the process and get medical attention as soon as possible.
When eye or face wash station is used, it shall deliver fluid at 0.4 liters per minute in both eyes at the same time. Any faster and could water damage eyes of workers.
Workplaces should have plumbed eyewash glass unit, however, you can use portable models. If portable eye wash station is used to provide it with the same amount of water. Having Eye Wash Station, portable or plumbed is not enough, though. To prevent secondary infection of the eye, the water must be treated to prevent the growth of bacteria and should be changed weekly and view. The unit as a whole, needs to be protected from airborne pollutants.
Because eyewash glass plants have to work at all times, water or liquid inside from freezing. The water should be between 60 ° F and 100 ° F 68 ° F to 77 ° F degrees is the ideal range.
When eye wash stations are put into work, all need to be 33 to 45 inches above the floor and six inches from the wall. The employee must be able to reach base in 10 seconds or less and be able to activate it soon. At the same time, the unit should be 10 to 20 feet from the danger zone.
Eye wash stations must be visible in the work environments and is located near the emergency exits. Clear the way to the station will be available, and signs need to specify the location of the unit.
Even with these stations kept in good condition and in the right places, workers need to know how to enable and use them. Due to chemical emergencies can happen at any time, require employees to be trained on using eye wash equipment installations.